Axial duct fan VS-2E-250 with grille and metal body, blade diameter Φ250 mm, supply voltage 220 VAC. Rated power 130 W and flow rate 1850 m3 / h.
- Industrial Fans and Blowers
- Industrial Fans
- Axial Fans And Blowers
- Axial Duct Fan, VS-2E-250, Ф250mm, 220VAC, 130W, 1850 m3/h
Axial Duct Fan, VS-2E-250, Ф250mm, 220VAC, 130W, 1850 m3/h
Axial fans are used when high flow rates are required. Low operational noise is an advantage when placed in ventilation shafts or ducts in industrial halls or public buildings. It is important, when choosing this type of fan, to take into account its characteristics so that they correspond to the particular application.
Axial duct fan
- model - VS-2E-250 with grille;
- blade diameter - Ф250 mm;
- body - Ф306x85 mm;
- operating voltage - 220 VAC;
- rated current - 0.55 A;
- rated power 130 W;
- flow rate - 1850 m3 / h;
- speed - 2600 rpm;
- number of poles - 2;
- joint type - bearing;
- operating temperature - from -40 ° C to + 60 ° C;
- noise level - 65 dB;
- maximum static pressure - 190 Pa;
- body - metal.
The fan is not allowed to operate under vacuum conditions (for example, the blower can take air out of a room that can not get enough air otherwise). This will result in insufficient airflow to cool the motor and the fan will be damaged.
It is possible to adjust the fan speed by means of a frequency inverter or by phase adjustment with a reduction of the speed up to 50%. The fan can not be powered by a DC / AC inverter with a modified sinewave - this will cause it to malfunction.